Question about Heating & Cooling
Central Heat (Gas) and Air system is blowing 3 amp fuses on control board. Unit specs follow: Carrier Product 58GP-050---111EA Model 58GP050-EA Serial # 2791A02092 Have replaced fuse, checked Ckt Brkrs and other fuses, manualy engaged compressor relay (outside), searched for any frayed or loose wires, replaced thermostat, bypassed Hi/Lo limit switches. Blower runs continuously, even with unit set to "OFF". Any Ideas????
Hi, Sounds like you have a short in the control circuit to me. Turn off all power going to the unit. Write down or otherwise mark the wires leaving the control board going to the thermostat. Remove them from the control board. Replace the fuse. Turn power back on and see if the fan still runs. If it does, check and or replace the heat limit switch that brings the fan on during the heat cycle. It may just need adjusted. If the fuse blows, I would think that the control board is probably bad. If it doesn't blow, Remove the thermostat. Leaving all thermostat wires open check them with an Ohm meter. There should be no continuity between them. Twist all the wires together at one end and ohm them again at the other end. You should have complete continuity on all wires. If the wiring checks out, down power the unit. Double check your wire colors and rewire the control board. With all wires open at the thermostat, turn the power back on. Touch the RED wire to the YELLOW wire. The Condensing unit should come on. Touch the RED wire to the GREEN wire. The fan should come on. Touch the RED wire to the WHITE wire. The heat should come on. Down power the unit. Replace the thermostat. Test unit. If the fuse has lasted ok but blows now it is either wired wrong at the Thermostat or the thermostat is bad. I hope I have helped. NOTE: If you can not understand these instructions. Call a licensed Heating / Air conditioning company. kstfas
Posted on Sep 23, 2007
Geiger-Air conditioning includes both thecooling and heating of air.
It also cleans the air and controls themoisture level.
Air Conditioning Contractors Directory for Cincinnati,
Prescreened Home Improvement Professionals for Cincinnati.
<a rel='nofollow' href="http://gogeiger.com/"> gogeiger</a>
Posted on Mar 20, 2008
Tips for a great answer:
Jul 14, 2014 | Carrier 52PQ-515---3 Premier Series Heat...
Aug 03, 2011 | Heating & Cooling
Jun 28, 2011 | Goodman CKL36AR36 Air Conditioner
Dec 03, 2010 | Carrier Heating & Cooling
Feb 23, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 22, 2009 | Goodman CLJ30AR32 Air Conditioner
Aug 09, 2009 | Carrier Heating & Cooling
Jan 04, 2009 | Carrier 52CQ-312-4 Comfort Series Heat...
1,605 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: