Question about Pramac GBW30P Encl Diesel Genset w/Perkins Eng
Posted by Anonymous on
Ensure any engine control switch is set to the run position, with the load disengaged. Manually set the air shut off valve (if fitted) to the run position (see Fig. 18), Turn the key switch to the start position, which will energize the solenoid allowing the engine to crank over for a few seconds then start.
Check the instrument panel is showing normal running oil pressure, and the ammeter for charge to the engine batteries.
Allow the engine to run for five minutes checking the instruments are reading correctly. Stop the engine and check the oil and coolant levels, replenish if necessary.
Posted on Aug 21, 2018
You run again the generator but before running, check & mark the oil level. Then stop the generator & wait until the oil settle to the bottom of oil pan. Check the oil level again & if the oil level is higher than the marking before that's means you have an engine gasket leak.You need to replace that gasket.
Posted on Mar 21, 2009
Check the fuel solenoid is getting power. It may be locked out by loow lube oil pressure and other things.
ALSO when restarting a diesel one OFTEN must "bleed" the fuel lines at each injector... same as when one inadvertently runs a diesel out of fuel. Crack the connectors at the injectors and crank till fuel comes out and tighten each one. Yes, it is a pain...
Posted on Apr 23, 2010
Tips for a great answer:
Jun 28, 2018 | Electrical Supplies
Mar 29, 2014 | Electrical Supplies
Dec 09, 2013 | Pramac GBW30P Encl Diesel Genset w/Perkins...
Jun 03, 2013 | Diesel Jlg Aerial Work Platform S2 Liftlux...
Oct 25, 2009 | Pramac GBW30P Encl Diesel Genset w/Perkins...
Oct 22, 2009 | Electrical Supplies
Mar 19, 2009 | Pramac GBW30P Encl Diesel Genset w/Perkins...
Mar 04, 2014 | Pramac GBW30P Encl Diesel Genset w/Perkins...
180 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: