Question about Goodman CKL24AR24 Air Conditioner
Posted by Anonymous on
This should have a time delay sequencer for the blower in the a/c mode. These are bad about being interminent in the a/c mode and also in fan. I have had some that would freeze up and I would get there and the fan be running. Thaw out and check and everything be ok. Got to cycling the fan on and off and sooner or later it would get where fan didn't come on. After replacement the customer didn't have anymore problem. Check the rely, looks like a heat sequencer but mounted on plate to blower compartment.
Posted on May 15, 2008
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
3 amp is standard.the fuse is blowing to protect the transformer.It is telling you that there is a short in the low voltage wiring.Goodman also had an issue with the coil shorting on the contactor.To prevent damage.....i'd call a pro.It should be a fairly simple repair.
Posted on Jul 04, 2008
Bad bearings on the motor or check the fan rotations . Air should always blow out the top and **** in through the sides or coils.!... Thank-you-very-much!
Posted on Aug 25, 2008
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
Tips for a great answer:
Jun 25, 2015 | Goodman Heating & Cooling
Sep 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Aug 27, 2009 | Heating & Cooling
Jun 03, 2009 | Heating & Cooling
May 28, 2009 | Goodman CKL60AR60 Air Conditioner
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
347 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: