Question about Goodman CKL24AR24 Air Conditioner
Posted by Anonymous on
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
When ever you hear a buzzing like you are hearing means one thing one of the fuses on the outside disconnect box is bad. Only getting 1/2 the power. Find the bad fuse and get the same size and will be good to go. ken
Posted on May 02, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
SOURCE: inside the air is blowing,
Two things; outside does the compressor try to come on? If not you may have a switch\Thermotat problem. Also make sure the breaker to the outside unit hasn't tripped. If it has tripped there may still be a problem after you turn the breaker back on. If it's only the fan that's not coming on outside you will need a new capacitor or fan motor and compressor(if the fan motor is replaced you should have a new capacitor also. If it has been intensely hot your unit might have just gotten overworked. Then resetting the breaker is all that is needed. If you have continuos resettings you MUST call a qualified HVAC Tech.
Posted on Jul 12, 2009
Tips for a great answer:
Jun 02, 2014 | Ruud Central System Air Conditioner
May 13, 2014 | Goodman CKL36AR36 Air Conditioner
Jun 23, 2011 | Goodman CKL42AR42 Air Conditioner
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Oct 07, 2009 | Goodman CLQ36AR49 Air Conditioner
Aug 17, 2009 | Heating & Cooling
Sep 13, 2008 | Goodman Heating & Cooling
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: