Question about Fahrenheat FFH1615 Heater
I need to install a used fan forced room heater. I don't know the correct wiring sequence to my power source. It is a 240/208 volt. It has two loose black wires, one from the temp control and one from the fan motor. also, a green wire that connects to the fan motor. No loose white wires visable.
You can be assured that the element is 240 volt. The fan motor is also rated at 240 volt. the wires you have black - black are the connections you make to the line. Use a 12/2 with ground. Use a double pole 20 breaker in your panelbox. The green wire is the equipment ground - connect this to the bare wire from the 12/2. On the 12/2 cable - there will be two colors, one black and one white. Wrap a couple of turns of black tape on the white wire both at the heater location and on the white in the panelbox. connect the 12/2 to your 2 pole breaker, the black wire and the taped white to the breaker.
Posted on Sep 06, 2007
Tips for a great answer:
Jan 28, 2014 | Hayward Industrial Products H400FDN...
Nov 30, 2013 | Coleman Propane Forced Air Heater...
Oct 19, 2013 | Coleman Heating & Cooling
Feb 23, 2018 | Goodman GMS90703BXA Heater
Sep 29, 2011 | 2006 Ford Escape
Feb 13, 2011 | Intertherm Heating & Cooling
Oct 01, 2009 | Fahrenheat Electric Hydronic Baseboard...
Feb 24, 2018 | Coleman Propane Forced Air Heater...
Oct 24, 2008 | Fahrenheat Electric Convector Baseboard...
Oct 07, 2008 | Honeywell Programmable Thermostat Heater
Aug 11, 2017 | Fahrenheat FFH1615 Heater
Dec 22, 2017 | Fahrenheat FFH1615 Heater
Usually answered in minutes!
Step 2: Please assign your manual to a product: