Question about Friedrich M18CF Split System Air Conditioner
I own a Friedrich air conditioning system with an external and internal unit. The system works well, but after 2 or 3 days of use, the internal fan blowing the cold air starts to make a rattling noise due to ice build up which gets in its way. After I shut off the system, the inside unit drips as the ice build up melts. I have cleaned the filters and this is not the problem. Please advise what would cause such a problem and potential solutions? Thank you.
Hi, Reduced air flow, low on freon or being continuously run during cooler weather such as at night. Some people turn their thermostat on 60 thinking that it will help get it cooler faster. They freeze up at night and don't get a chance to thaw during the day. It needs set no lower than 75 or so. The evaporator may be dirty. Don't know a lot about your particular unit but if the outside unit has the compressor and refrigerant lines running to it, The large refrigerant line should sweat all the way to the compressor if its fully charged. Please rate me if I have helped. Good luck kstfas
Posted on Aug 28, 2007
You may have blocked a return vent with furniture or something if so pull it away from the wall a little bit but you have to let it thaw all the way out before you turn it back on
Posted on Jan 07, 2014
1.Improper airflow (dirty filter,faulty blower fan, closed or blocked registers,etc)
2.Low refrigerant charge (possible leak)
3.Restricted liquid line (kinked)
Can all cause freezing of the evaporator (indoor coil)
Posted on Aug 22, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 06, 2013 | Dometic Rooftop RV Air Conditioner
Feb 29, 2012 | Friedrich Heating & Cooling
Sep 07, 2011 | Friedrich MW12Y3FM Split System Air...
Jul 19, 2011 | Heating & Cooling
Jun 22, 2010 | Heating & Cooling
Jun 08, 2010 | Friedrich CP24E30 Air Conditioner
Aug 20, 2008 | Friedrich Heating & Cooling
Jul 26, 2008 | Friedrich QuietMaster Electronic SS12J30D...
Jun 01, 2008 | Friedrich D50C Dehumidifier
Apr 14, 2011 | Friedrich M18CF Split System Air...
1,403 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: