Question about Generac 13,000 Watt / 13,000 Watt Home Standby Generator
Typically caused by the fuel line (LP or Natural Gas) having a lot of air in it. Was your generator just installed, or was there any work done to the gas line of the building / generator? Consult local gas contractor / propane dealer / gas company for assistance in purging the fuel line.
A low battery can also cause this as well as the generator is not able to come up to starting speed quick enough. Try placing a stand alone battery charger on the generator and charge the battery. Also check the air filter as well.
OverCrank condition occurs when generator tries to start itself, or be manually started, and the starter spends too much time turning.
This can also indicate failure of the control board. This will need the expertise of generac technician. Call 1-888-GENERAC (1-888-436-3722)
M-F 7am-6pm Central
Posted on Aug 25, 2009
Tips for a great answer:
Feb 05, 2017 | Cars & Trucks
Sep 03, 2015 | Cars & Trucks
Aug 25, 2015 | Heating & Cooling
Jan 09, 2013 | Acer Aspire Computers & Internet
May 07, 2011 | Computers & Internet
Nov 27, 2010 | 1987 Plymouth Voyager
Apr 23, 2010 | Craftsman Garden
Jan 12, 2010 | Dell Dimension 4600 PC Desktop
Sep 02, 2009 | E-Machines eMachines Desktop PC
Oct 10, 2016 | Generac 13,000 Watt / 13,000 Watt Home...
1,576 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: