Question about Goldstar R5050 Air Conditioner
In the back of the compressor housing under the fan water will accumulate until the fan hits it.What is causing this water issue? The drain hole is clear.
This is the normal operation of most window units. It this is the case on your particular unit you will notice a slinger ring on the outside of the fan blades which slings water created from the evaporator and drained into the condensing area. The water is slung into the condenser making the unit cool more efficiently. The water drain hole will remove excess water. The earilier explaination may be needed if the water is dripping inside the cooled space. Tilting the unit back slightly may also be needed. Hope this helps. kstfas
Posted on Aug 27, 2007
You will need to clean the evap coil with a bleach type product and then hose out the condenser coil as well. The bleack will also remove algie from the evap water pan. THX RepairUSA
Posted on Aug 26, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 07, 2014 | Samsung RF4287HARS Stainless Steel French...
Jan 18, 2010 | GE Refrigerators
Oct 24, 2009 | Porter Cable Cable 135 PSI, 60 Gal. Oil -...
Oct 19, 2009 | Maytag Refrigerators
Aug 22, 2009 | GE Profile 26.6 cu. ft. Side-by-Side...
Aug 14, 2009 | Samsung AS1293L Air Conditioner
Jun 17, 2009 | Heating & Cooling
Jun 02, 2008 | Goldstar DH5010B Dehumidifier
290 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: