Question about Fahrenheat Electric Hydronic Baseboard Heater, 240 Volt

# I have 2-240V (4.2V) basebaord heaters, Need Wiring Diagram

Hello, Buddy of mine ran 10/3 Wire for 2-240V baseboard heaters & Has a 120/240V 2-Pole 20AMP Breaker. Question for you ? He shouldn't of used 10/3 Wire for this 240V equip. The Red wire is not going to be used, correct ? As far as the 2-Pole Breaker, I will be attaching the white wire in the 2nd slot on the 2-pole breaker ? Do you have a Wiring Diagram ?

Posted by on

• chris bil Mar 22, 2009

What about at the breaker, tie red & black into 2-Pole Breaker, Attach Ground. What about Neutral ?

• chris bil Mar 22, 2009

Thanks, You have been a great help.

×

### Anonymous

• Level 2:

An expert who has achieved level 2 by getting 100 points

MVP:

An expert that gotÂ 5 achievements.

Governor:

An expert whose answer gotÂ voted for 20 times.

Scholar:

An expert who has written 20 answers of more than 400 characters.

• Expert

You get 120V from any phase (black OR red) to neutral
you get 240V from phase to phase (between black and red) and in this scenario you don't need the white wire.
So for you, connect the black to 1 pole of the breaker and the red to the other pole, connect the green wire to the ground strip and you are done.
A white wire is NEVER connected to a circuit breaker anyway, it is a grounded wire, it would be like connecting a green wire to a black wire, bad idea.
the National electrical code specifies red and black wire color for 240VAC circuits.
As Ask Hank mentionned, nothing wrong with 10/3 wire.

Posted on Mar 22, 2009

### HANK MCNEIL

• Level 2:

An expert who has achieved level 2 by getting 100 points

All-Star:

An expert that gotÂ 10 achievements.

MVP:

An expert that gotÂ 5 achievements.

Vice President:

An expert whose answer gotÂ voted for 100 times.

• Fahrenheat Expert

Nothing wrong w/ 10/3 @ 20A. use the red and black and don't use the white. dosent matter which is which (blk and red).

Posted on Mar 22, 2009

• HANK MCNEIL Mar 22, 2009

no neutral w 240V - 2 hots and ground

×

×

my-video-file.mp4

×

## Related Questions:

### I need to wire a remote thermostat to my electric wall heater in the bathroom. Not sure if I run the wire from the panel to the heater first or to the remote thermostat then the heater.

Run the wire to the thermostat then to the heater

BASEBOARD WIRING WITH A SINGLE POLE (2 WIRE) WALL THERMOSTAT - 120V OR 240V SUPPLY

BASEBOARD WIRING WITH A DOUBLE POLE (4 WIRE) WALL THERMOSTAT - 120V OR 240V SUPPLY

Jun 21, 2011 | Heating & Cooling

### Bought a Fahrenheat 5' baseboard heater and a single pole thermostat to replace an old heater. What's the difference between a single and double pole thermostat? Which should I use? I have a 240v line...

Here is a link to the wiring instructions, which has detailed pictures and instructions. This should make it a lot easier. http://www.marleymep.com/en/multimedia-library/pdf/fahrenheat-pdf/products/f2500-series/F2500wiring.pdf

Feb 14, 2011 | Fahrenheat F2545 Electric Baseboard Heater

### Can a 240 volt outlet be ran off this breaker and can a 240 volt electric baseboard heater be wired to it or should i use double pole breaker?

You need 240 breaker:
Notice that your 240V breaker is twice as wide as regular 120V breaker.
Notice that both switches are tied together on 240V breaker, making this a double-pole breaker.
http://waterheatertimer.org/See-inside-main-breaker-box.html
http://waterheatertimer.org/B220C.html

Jan 24, 2011 | Siemens 20 Amp Single Pole Breaker 120/240...

### I have a large room in my basement where I would like to install four Marly 58" baseboard heaters to work off one thermostat. The units are rated at 1250 watts each for a total of 5000watts. I plan to...

Using the equation I = P/E where "I" is Amps, "P" is Watts, and "E" is voltage, we find that your 5000w circuit will have an Amperage of 20.83. A 22 amp tstat will work, it will just leave you no room for surges. I would suggest splitting the baseboard and using 2 thermostats. Hope this helps

Aug 10, 2010 | Marley Electric Hydronic Baseboard Heater,...

### No i didn't. I need instructions for wiring a

you have baclk and red wire supply and a black and red wire to load (baseboard).
your switch will have 2 black and 2 red.
connect blk supply to 1 black on switch ( it doesn't matter which one)
connect red supply to 1 red on switch
then
connect black from baseboard to black switch
connect red from baseboard to red switch
if multiple baseboards that have several loads at thermostat then just connect baseboard blacks together and reds together before connecting at switch.

Oct 17, 2009 | Heating & Cooling

### Properly installed electric baseboard heater won't work.

I am an electrician. You must measure the voltage across the black and red wires. Measuring each wire to the neutral will not cut it. If both your red and black wire are on the same phase the heater will not work.

To double check your wiring, measure the voltage across the two screws feeding your subpanel, they should be 240v or 208v depending on your power company. Then do the same at the breaker feeding your thermostat. Again it should read 240v.

If you have no potential across the screws it is possible that you installed an incorrect breaker. Not all breakers with two screws on them are 240v breakers. There is what is called a twin or split breaker that has two screws that are on the same phase. These are for wiring two 110v circuits, when you run out of spaces in the panel.

Double check everything. This is a relatively easy circuit to wire, even for homeowners. If the heater does not work them something is wrong so do not leave the circuit energized.

Nov 22, 2008 | Fahrenheat Electric Convector Baseboard...

### Please i need help with 240v wiring to heater

i have the answer, i just did mine...though u already have your answer since this post was published a while back ago...if not write me back...

Sep 12, 2008 | Fahrenheat Electric Convector Baseboard...

3,839 views

Level 3 Expert

Level 3 Expert