Question about Hampton Bay 04383 Calibre Ceiling Fan
I am installing a Hampton Bay ceiling fan after taking down and old inoperable fan. I have two switches (fan and light) AND the light is on a three way switch. The Hampton Bay has a remote control and the transmitter controls both fan and light on one power source. How do I install this thing?
In your ceiling box should be three wires. a red goes to the three way switches, a black goes to the hot and the white is the neutral. the fan wires are black, blue and white. since you have a remote, connect the [fan] blue & black together with the [line] black. connect all white wires together. the remote will now ramp up your lights from off to full on and the fan remote will let you choose lo med high and off. just tape up the red wire in the box.
Posted on Aug 22, 2007
I have a hampton bay ceiling fan with light fixture all connected to a wall switch and controled by a remote. The light does not work any more and I have replaced the bulb with three different light bulbs and it still won't work. There is a green wire coming off the bracket but there is no ground wire coming in from above. There are two wires coming in from above ( the box in the Attic)
one white and one black and they are connected properly. All the wires are taged from the remote receiver, the fan and the light and are correctly connected. Any suggestions?
Posted on Mar 30, 2008
Tips for a great answer:
Nov 21, 2016 | Hampton Bay Dryers
Oct 05, 2016 | Hampton Bay Dryers
Oct 15, 2012 | Hampton Bay Ceiling Fan. Trieste 52 in....
Aug 07, 2012 | Hampton Bay AC418-OBB 60'' Brookedale Oil...
Nov 05, 2010 | Hampton Bay 52 In. White Redington...
Jun 02, 2010 | Hampton Bay 52 In. White Redington...
May 19, 2009 | Hampton Bay 13087 70450 Carousel II...
Usually answered in minutes!
Step 2: Please assign your manual to a product: