Question about GE Zoneline AZ38H12DAD Split System Air Conditioner
COMPRESSORS HAVE AN INTERNAL T-STAT TO PROTECT THE WINDINGS ... SOME THING IS CAUSING YOUR COMPRESSOR TO RUN "HOT" THIS WILL KICK "IN & OUT" THE COMPRESSOR DURING COLLING OPERATION AND HEAT MODE (IF IT IS A HEAT-PUMP). 1ST THING TO EASILY CHECK IS THE CONDENSOR "OUT-SIDE" COIL. (CLEN BOTH WHILE YOU ARE AT IT). THESE FANS PULL THE AIR IN AND A BLOW OUT THE COIL .... ALL THE DIRT WILL BE ON THE INSIDE. 2ND THING IS THE FAN ITSEL OVER HEATING AN TURNING "OFF" ON ITS OWN "BUILT-IN POTECTION T-STAT". THIS WILL GIVE YOU THE IRRATIC OPERATION YOU ARE DESCRIBEING. I TEND TO THINK IT IS YOUR FAN MOTOR ... EASY TEST. TURN "OFF" EVERYTHING BUT THE FAN. SET IT FOR MANUAL "RUN ALL THE TIME" POSITION. THE FAN SHOULD NOT KICK OFF !!! IF IT DOES YOU FOUND THE PROBLEM. IF IT DOES TURN OFF IT CAN BE A WEAK CAPACITOR. UNITS VARY ON WETHER THE CAPACITOR IS FOR COMPRESSOR/FAN OR HAS A SEPERATE CAPACITOR FOR EACH. CAPACITORS ARE NOT EXPENSIVE. HOPE THAT CAN NARROW YOUR PROBLEM DOWN
Posted on May 07, 2007
I have found that my unit has a 2 min delay module inside the outdoor unit and it was bad which made the unit cycle on and off or just not at all . I fixed that myself after finding the part and it was simple to do .
Posted on Sep 12, 2012
Tips for a great answer:
Apr 30, 2016 | Kenmore Refrigerators
Sep 07, 2015 | Amcor Heating & Cooling
Oct 19, 2013 | Frigidaire Refrigerators
Sep 17, 2017 | GE Heating & Cooling
Jan 17, 2018 | Ruud Heating & Cooling
Apr 02, 2011 | GE Zoneline AZ35H12D Air Conditioner
May 31, 2010 | Dometic Rooftop RV Air Conditioner
May 02, 2010 | Heating & Cooling
Dec 20, 2008 | Heating & Cooling
Aug 23, 2017 | GE Zoneline AZ38H12DAD Split System Air...
Jan 15, 2014 | GE Zoneline AZ38H12DAD Split System Air...
Usually answered in minutes!
Step 2: Please assign your manual to a product: