Question about Rheem 50 Gallon FVR NATGAS Water Heater 6YR 22V50F1
You have Honeywell electronic gas control valve, and error code is 7 flashes.
Probably you have power vent model.
One manual from different company says: "Reset gas control using on-off button on front of control, replace flammable vapor sensor, replace gas control thermostat.
But with Rheem you also need specific steps: Remove gas burner and look for broken glass vial, and then blow out arrestor screen air intake using compressed air, clean burner parts, check for unobstructed venting, you will need new glass vial from Rheem depending on year and model number of water heater that appears on label on side of unit, or they may not have a repair kit for that model, and you might need a new gas control valve depending on model and how extensive problem was
You have Rheem water heater.http://waterheatertimer.org/How-to-repair-Rheem-FVIR.html
If you need further help, I’m available over the phone at https://www.6ya.com/expert/gene_9f0ef4df2f9897e7
Posted on Sep 28, 2012
The water heater is locked out. The following process should reset it.
1. Reapply power to the water heater and wait for 3 seconds for the system self-diagnostic check.
2. Within the first 30 seconds, the temperature dial must be rotated back and forth crossing the 120
degree mark at least six (6) times. This will reset the control and display a normal flash code
Posted on Apr 20, 2009
there is a screen around the bottom of the unit? if so take it off and clean it,, does this unit have a self ignitor, or is it piliot? make sure your flue is clear so the unit is not over heating,, make sure on the power vent that the filter is clear also,, does the fan come on before the gas ignites, if not the circuit board is going bad the fan should start first to omit the gas fumes
Posted on Jun 06, 2009
Flashing code 76 is lost communication between the remote and the burner control assembly CCA (circuit card assembly). The CCA is still under warranty if purchased within the last 3 yrs. Contact Rheem customer service and have your Mod. and S/N available....explain to the agent you are recieving - flashing code 76...they'll walk you through the process.
Posted on Nov 01, 2009
"Pres sw open" means there is insufficient air flow. either the vent if blocked, or the blower turns too slow/ or died.
Posted on Feb 12, 2010
The flashing light is a trouble sequence light. Find your manual to see what 4 flashes means. It's usually attached to the side of the water heater tank. Try a quick fix by unplugging the power vent and see what happens.
Posted on May 15, 2010
Tips for a great answer:
Usually answered in minutes!
Step 2: Please assign your manual to a product: