Details I have a problem with a Goodman Model GSH130601AA, ( 5 Ton, 13 Seer heat pump) central air unit, installed 06/15/2006. (I know, I saw online reviews but unit was put in before I saw negative e
The fan motor is bad and needs replaced. Depending on how mechanically inclined you are, you can replace it yourself fairly easy, the hardest part being the fan blade without a hub puller. Just take your old one in with you to a local A/C supply store. The compressor is more than likely kicked off on thermal protection because of the fan motor, happens every time. After the compressor cools back down, the overload kicks back in and the compressor will start. I would also replace the capacitor while I was there, just for preventive maintience because they go out all the time, plus they are cheap. Just make sure you have the full 220v to the unit before diagnosing the problem, and make sure it is completely off when working on it, capacitors hold a charge, just in case you didn't know already. As for the Goodman problem, people never give the full story behind these units. For one, it may say Goodman on the cover, but the motor and compressor are made by the same companies other brands use, just look at the compressor brand, probably a Copeland or a Bristol used in various brands. Two, the reason that there are more negative things said about these units are simple, more units sold, more people have them, there will obviously be more to talk about. Kind of like more money, more problems. Nothing is built like it was 15 to 20 years ago. Goodman keeps their price low by not advertising for the most part. And then you have units like Lennox that are supposed to be good, cost more to buy, and absolutely too expensive when repairing and finding parts. Just so you don't think I'm a Goodman rep or anything, I prefer American Standard equipment over anything else Ha! This is of course all from a service aspect from dealing with this everyday, but still just an opinion. I hope I have helped you and get you to cooler days, and sorry about going on and on, just thought you might like a view from someone on the inside! Have a good one and good luck!
Jun 28, 2012 |
Heating & Cooling