Question about Jenn-Air JED8430 Electric Cooktop
This answer does not solve the question regarding what to do with the red wire??
Posted on Jun 18, 2008
You do need a 208/240 volt supply from your service panel. The green is ground, white is nuetral, and the red and black should measure 120 volts each to ground or 240/208 between each other. It is normal for most breaker panels to supply 208/240 between adjacent insulators. If you are only getting 1/2 of that then the circuit breaker may not be straddling the insulator bar but be 1/2 notch out and both breaker pins contacting the same 110 supply.
Posted on Apr 16, 2007
Tips for a great answer:
Usually answered in minutes!