Question about Rheem Heating & Cooling
Model# aof 14f 201
Posted by Anonymous on
Check all your manual reset limits. There are two wires that go to a small disk about the size of a penny. In between those wires is a small button. Press the button firmly. You will have between 2 to 5 of these. There is also a limit switch located on the back wall of the unit that enters in the heat exchanger but it is not resetable that could be bad. You will need to check all of these. They can be jumped temporarily by removing the wires and adding a small wire.
Posted on Apr 06, 2009
Tips for a great answer:
Jan 02, 2016 | FACTORY AC PARTS Limit Switch Double Pole...
Dec 16, 2015 | Heating & Cooling
Oct 11, 2015 | Heating & Cooling
Oct 19, 2012 | Rheem Gas Furnace 60000 Btu 95% Afue. Rgrc...
Mar 06, 2011 | Rheem 50 GAL ELEC TALL Water Heater 6YR SC...
Feb 18, 2010 | Heating & Cooling
Dec 23, 2009 | Honeywell Electronic Programmable...
Nov 25, 2009 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Dec 09, 2008 | Heating & Cooling
140 people viewed this question
Usually answered in minutes!