Question about Rheem Heating & Cooling
Posted by Anonymous on
Do you have 4 wires going to you thermostat and do you have an R and Rh terminal or R and Rc terminal on your new thermostat?
If so then you need to put a jumper wire from R to Rh or R to Rc.
Posted on Jan 04, 2010
Tips for a great answer:
Nov 17, 2014 | Rheem Air Handler 3 Ton With RBHP Series
Nov 20, 2012 | Rheem Gas Furnace 60000 Btu 95% Afue. Rgrc...
Oct 23, 2011 | Heating & Cooling
Jan 13, 2010 | Ruud UAMB042 Air Conditioner
Dec 31, 2009 | Heating & Cooling
Nov 25, 2009 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Aug 16, 2009 | Heating & Cooling
Jan 07, 2009 | Weather King 12AJA4801AH Air Conditioner
Dec 09, 2008 | Heating & Cooling
445 people viewed this question
Usually answered in minutes!