Question about Sanyo STW0923H2 Thru-Wall/Window Air Conditioner
I have a Sanyo through the wall heat pump unit. When I plug it in the heater coils start heating even with the dial in the off position. No matter where I turn the dial; heat,fan, or cool the heater coils stay on. The compressor seems to be working fine and the reverse switch seems to be working but with the electric heating coils on all the time of course all I get is heat. This is also very dangerous because as I said the coils stay on even with the fan off causing the unit to overheat and start smoking. Any help is sincerely appreciated.
We use the STW0925H! in 60 rooms on this property and have encountered similar problems that were caused by weldedd contacts on one of two relays that controls the electric strip heat. They can be replaced if needed.
PTHP's and PTACs employ thermal fuses as well as a bimetal limit stat on the heating element to limit risk if fan motor were to fail and the heating element were to remain energized. It would be wise to check that both are fuctioning properly while you are servicing the unit.
Posted on Mar 07, 2008
I suggest that the thermostat or the switch is at fault, contacts may be stuck. hope this helps
Posted on Mar 04, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 11, 2015 | Heating & Cooling
Nov 17, 2012 | Heating & Cooling
Jul 11, 2012 | LG Heating & Cooling
Apr 30, 2011 | Dryers
Apr 03, 2011 | GE Dryers
Dec 24, 2009 | Maytag Neptune MDE5500AY Electric Dryer
Nov 03, 2009 | Carrier 52PQ307 Wall/Window Air...
Dec 13, 2008 | Amana Haier AP125HD Air Conditioner
211 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: