Question about Soleus Mini Split 12000 BTU A/C Air Conditioner
Due to our location, Soleus will not honor warranty on my split system a/c, KFR-1200. They have sent me a replacement squirrel cage for the air handler. (Original cage was damaged by loose piece of metal.) Can anyone advise me how to get the squirrel cage out and the new one in? Thanks.
You have to take blower out by removing the 2 screws that is holding it ,then you loose the motor shaft from wheel by using a Allen key .Once motor shaft is loose you then loosen motor frame from housing and slide motor out .Might have to spray it with wd 40 .
On the housing should be some screws along the side so you loosen those and house ing would open up so you can get wheel out.
To install you reverse the process.
Please note the direction of the old wheel because if install backwards will not work right
Posted on Feb 14, 2018
All of the kfr series have a indoor coil sensor that monitors the tube temperature. In the heating mode it will sense for high temp and cut off the outdoor fan to try to lower the indoor coil temp. The cut off temp is 129f, when the coil cools down the fan will cut in and start developing heat again. If the coil continues to get warmer it will shut off completely. The system is either overcharged or the coils and or filters are dirty. All Soleus units need both lines insulated seperately and not together because the metering device is in the outdoor unit. Have your tech calibrate the charge and make sure you clean your filters every 3 months. Removing the sensor will cause the indoor coil to get too hot and possibley start to melt your housing. For further technical questions pleas call 626-378-1518 for technical questions,,professionals only.
Soleus Tech Support
Posted on Mar 13, 2009
Tips for a great answer:
Usually answered in minutes!
Step 2: Please assign your manual to a product: