Question about Empire GWT-25 Wall Mounted Panel Heater
I dont know where the power to my t-stat is coming from from my wall furnace. how do I check that with my multimeter. i have heat only
How is wires connecting to thermostat Honeywell to empire walls heathers GW-25-5
Posted on Dec 19, 2014
My wall empire w35-6 wall heater is not connecting to the thermostat, what should I do?
Posted on Dec 11, 2007
Look inside the control panel of the heater. look for a 120 volt to 24 volt transformer. There may be a fuse on the transformer secondary. The thermostat switches a hot 24 volt wire so you won't find a common at the thermostat.
Posted on Oct 15, 2007
Tips for a great answer:
Sep 19, 2011 | Heating & Cooling
Mar 11, 2011 | Coleman Heating & Cooling
Jan 12, 2011 | Honeywell Programmable Thermostat Heater
Nov 23, 2010 | Honeywell Programmable Thermostat Heater
Jan 18, 2010 | Coleman Heating & Cooling
Nov 02, 2017 | Goodman Heating & Cooling
Dec 10, 2009 | Heating & Cooling
Oct 24, 2008 | Heating & Cooling
Oct 02, 2008 | Kitchen Appliances - Others
Jun 29, 2017 | Heating & Cooling
Mar 29, 2017 | Empire GWT-25 Wall Mounted Panel Heater
Dec 28, 2008 | Empire GWT-25 Wall Mounted Panel Heater
309 people viewed this question
Usually answered in minutes!