Question about Aprilaire 1120 Humidifier
Kurt, a couple of things you can check. First when you turn the humidistat do you hear a click from the solenoid? This would indicate that you are in fact getting power. Check the saddle valve from the supply. Turn it in and out to make sure it is not clogged. You should have a inline strainer on the inlet side of the valve. Make sure it is not clogged with deposits. On the discharge side of the valve should be an oriface, make sure that is clog free. If you have an meter you can check for power at the soleniod or pull the harness off and ohm it. Should show continuity. Catriver...post back.
Posted on Oct 15, 2006
Tips for a great answer:
Usually answered in minutes!
Step 2: Please assign your manual to a product: