Question about Generac 13,000 Watt / 13,000 Watt Home Standby Generator
Need correction info
See my 5/22/12 comments on my "overspeed fault" problem resolution [Generac 43903 standby Generator overspeed indicator on starting] . If it only runs for a few seconds and then quits, you may have a similar condition to the one my unit had. A good technician should be able to diagnose the problem and determine if you have a similar failure to the one I had, or one of the other causes suggested by RSG000.
Posted on May 23, 2012
I work on these every day. Its either gonna be the rotor or stater, the voltage regulator, but most likely its a bad stepper motor which is the throttle motor, or control board. Thats all that could be causing that so its one of those. If its the rotor or stater thats bad it causes the generator to RPM up because it thinks its not producing enough power due to that. I had the same problem with the same one we just fixed and it was the slip rings on the end of the rotor so bad rotor.
Posted on Jul 09, 2009
Tips for a great answer:
Jul 20, 2018 | The Computers & Internet
Jan 26, 2018 | Opel Cars & Trucks
Feb 20, 2016 | Computers & Internet
Mar 13, 2014 | Alinco Radio Communications
Oct 19, 2013 | Whirlpool Dishwashers
Mar 18, 2011 | Sony Grand WEGA KFE50A10 50" SDTV LCD...
Jun 24, 2010 | Medical
Dec 12, 2009 | Yahoo Mail
Oct 10, 2016 | Generac 13,000 Watt / 13,000 Watt Home...
2,172 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: