Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
Raypak RP 2100 was working fine. Propane was low (30%) and the heater wouldn't come on. It would CFH, then SPK over and over but would never ignite. I thought the gas was low, filled the take, it still just sparks over and over but never lights. eventually turns to a LO code.
Posted by Anonymous on
Well your right it is your ignighter the spk is spark the plt piolet light this pc is about 200 .
THANK YOU FOR USEING FIXYA
Posted on May 03, 2009
Make sure that gas control knob is set to ON (counterclockwise).
Make sure that ON/OFF switch is ON.
Check that temperature setting is high enough to call for heat.
Make sure pool pump is running and water is flowing to unit.
If not above there is a diagnostic procedure on page 33 of manual at:
Posted on May 30, 2009
The CFH is a Call For Heat.
The SPK tells you that it is creating a spark for ignition.
The LO tells me that you are on propane.
The fact that it doesnt light tells me that either the ignitor is not sparking, or that there is no gas, or an incorrect gas supply.
If this unit is installed with flexible gas line, replace this with rigid black pipe or a larger flex line.
Posted on Nov 04, 2010
Tips for a great answer:
Aug 12, 2011 | Raypak 130,000 BTU Propane Gas Pool...
Oct 11, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Aug 03, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Oct 24, 2009 | Raypak Free Hydraulic Lift Gate Delivery -...
428 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: