Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Why does my heat pump ice up in Winter?
Heat pumps naturally ice-up in the winter. It is normal for the entire coil to be covered in a white frost and even light ice, during cold weather conditions. However, it is bad for the entire unit to be encased in ice. This indicates ductless heat pump problems which should be addressed quickly to save energy and avoid serious damage to your ductless unit. These systems should periodically go into a defrost cycle. This keeps the unit running efficiently. If the coils are blocked by ice, proper heat transfer between the coil and the outside air will not occur.
How does the defrost mode work?
When the mini split heat pump goes into defrost, the reversing valve inside of the outdoor unit is energized, switching the system from heat to the air conditioning mode. The outdoor coil becomes the hot, the indoor coil becomes cold, and both - the outdoor and indoor fans shut off. This allows the outdoor coil to melt accumulated ice. When the built-in micro-computer analyzes that all ice have been melted, the heat pump heating system goes back to heating mode.
A cloud of water vapor may be seen rising over the outdoor unit and a "whoosh" sound can be heard as the refrigerant reverses direction. The entire process usually takes up to 10 minutes (depending on conditions).
How often does the system goes into defrost mode?
Ductless mini-split heat pumps have different ways of determining when to go into defrost. The built-in microcomputer determines outdoor temperature, refrigerant pressures, and several other factors. In colder temperatures the system will go into defrost more often than in warmer.
If a ductless mini split heat pump is severely iced-up in the winter it is possible that it isn't defrosting (though there could be many other causes). Let the manufacturer certified technician check your system
Posted on Jan 16, 2013
This is fan only No ac at this time no heat pump I just need to run the fan at different speeds
Posted on Jan 24, 2012
SOURCE: heat pump not running
check your house circuit breakers first that should be labeled heatpump or outdoor unit
make sure it is on and or not tripped
then if you have a box outside near the outdoor unit open it up and see if there is a breaker or maybe fuses that could be blown
Posted on May 26, 2009
Tips for a great answer:
Mar 01, 2017 | Heating & Cooling
on Jan 30, 2010 | Heating & Cooling
Jan 30, 2016 | Amana PTH153B50AJ Heat Pump Air...
Jan 24, 2016 | Mitsubishi Electric Mr Slim E12C26426...
Feb 13, 2015 | Heating & Cooling
Dec 27, 2014 | Heating & Cooling
Dec 02, 2013 | LG LSN122HE / LSU122HE - 11,500 BTU 13...
Feb 01, 2010 | Honeywell Programmable Thermostat Heater
Jan 22, 2010 | Heating & Cooling
Jan 16, 2009 | Heating & Cooling
789 people viewed this question
Usually answered in minutes!