Question about Goodman CKL30AR30 Air Conditioner
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: My Goodman CKL30-L1 is turning
access the electrical cover on the corner of the unit after disconnecting power and inspect for loose wires or bad capacitor, the capacitor has three different terminal connections on top and the top should be flat not bulged, if bulged,rounded in any way then the capacitor needs replaced. If the fan motor still does not work, then the motor will also need replaced. Note: capacitors can go bad without bulging or swelling, a meter for testing capacitors will verify uf(MFD)rating as printed on part.
Posted on Aug 24, 2011
It sounds like the blower motor has burnt up.(the one inside) The unit running for a few minutes then shutting off, is due to the high pressure/temperature safeties. When you removed the panels, did you notice any fan running?
Posted on Feb 19, 2008
If you are sure of the power then ya have a control problem thermostat set correctly? could be open low pressure switch I would call for service. Tom
Posted on Jul 03, 2009
Look at the contactor on the condensing unit, remove the low voltage wires to the contactor and turn on the system. If the low voltage fuse doesn't blow, replace the contactor.
Posted on Jul 07, 2009
Tips for a great answer:
Oct 25, 2013 | Goodman Heating & Cooling
Sep 02, 2011 | Goodman CKL49AR49 Air Conditioner
Aug 16, 2011 | Heating & Cooling
Mar 31, 2010 | Goodman CLQ36AR49 Air Conditioner
Apr 28, 2009 | Goodman CKL60AR60 Air Conditioner
Apr 27, 2009 | Heating & Cooling
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
173 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: