Tip & How-To about Refrigerators
It would help to have refrigerant type.
The pressures will vary according to load, as when it is first started up. The best way is to weigh the amount of refrigerant charged. By charging by feel, can read the compressor current draw, it is safe to not exceed 1/6th of the compressor LRA. Can charge slowly by filling the evaporator to feel cold refrigerant from entrance to exit.
Condensor may fill with the bottom 1/3 cooler than the hot/warm top. Overfilling will overload the compressor, frost appears on the suction line, first portion of the evaporator may not cool off and actually be warmed.
Posted by J Rosado on
Jun 27, 2017 | Health & Beauty
Dec 25, 2017 | Hoover Washing Machines
Sep 23, 2010 | Hoshizaki Freezer Commercial Ice Machines...
May 20, 2009 | Amana 22.6 cu. ft. Side-By-Side...
Jan 10, 2009 | Amana DRB1901C Bottom Freezer Refrigerator
215 people viewed this tip
Usually answered in minutes!