20 Most Recent
Questions & Answers
I know this is late but I had to add a solution to this problem since I had the exact same problem and was able to solve it. The probelm is not your control board. On these units, the heat pump compressor will not kick in unless the temperature you set on the control panel is within 2-1/4 degrees (or 4 degrees depending on your unit model. Otherwise, the unit locks out the compressor until the electric heat coil bring the indoor temperature up to that level - and then will switch the compressor back on for heat pump operation. So the problem is not the control panel or the compressor, it the electric heat coil. The coil has two manual limit switches on it that may be tripped and should be checked. The coil can be easily accessed by shutting down the power, removing 4 screws around the air outlet, pushing the screen up and sliding the panel out the top. The power wires can remain in place while the limit switches are reset. Hope it works.
on Apr 20, 2020
I have an electric fire and it was working fine
Your question is worded strangely, did you have an electrical fire in the unit? My guess is that you have not kept the filter clean and now you need to take it to a service company for the replacement of the heater's fuseable link.
on Oct 09, 2009
Heater blowing out cold air
Yes you could have a bad overload on the heater element which is fairly simple to fix. To test for this pull the heater out and get an ohmeter set it to continuity and check the continuity first through the entire heater element then if there is none pin point the overloads and check to see which one has no continuity.
on Dec 07, 2008
Replacing an amana mercury thermostat with honeywell programmable. Old wires are y1,w1,w2,g,rc/rh. Have y1 to y, w1 to o/b, w2 to aux, r to r, g to g. Now outside will not shut off when heat is on.
What is -the outside?
Heat pump, gas, electric heat combination?
You may need to back track, double check the Honeywell configuration jumper or software settings for your type of heating used.
Amana Heating &...
on Nov 09, 2019
Not finding what you are looking for?