Mr. Heater... | Answered on Dec 11, 2017
Mr. Heater... | Answered on Dec 03, 2016
Mr. Heater... | Answered on Dec 16, 2015
Mr. Heater... | Answered on Sep 07, 2015
Mr. Heater... | Answered on Mar 28, 2015
Mr. Heater... | Answered on Nov 20, 2014
Mr. Heater... | Answered on Jul 03, 2014
Mr. Heater... | Answered on Jul 01, 2014
Mr. Heater... | Answered on Feb 19, 2014
Mr. Heater... | Answered on Jan 31, 2014
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor.If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Mr. Heater... | Answered on Jan 27, 2014
88 questions posted
Usually answered in minutes!
Step 2: Please assign your manual to a product: