20 Most Recent
Questions & Answers
It will turn over once or twice and stops it has a red light on where the braker panel is
press the helpful button and follow me on Fixya for more helpful tips
The current models of automatic standby generators will have LED indicator lights on the side compartment of the generator. A green LED light will indicate that the unit is in AUTO mode and is ready to run, or is running properly during a utility outage. The yellow LED light will indicate that maintenance is needed. The red LED will indicate either that the unit is switched to OFF or that there is an alarm detected. If a yellow or red LED are present, you will need to check the generator's control panel, as it will describe the type of maintenance needed or the alarm present. This information can be found in the owner's manual as well. You can find a copy of the owner's manual online by searching the model or serial number of the unit here
on Jan 27, 2016
One cylinder not firing on generator
If you have spark and compression and it not firing then you must not have fuel. the fuel is fed from the demand regulator thru the intake independent for each cylinder. Check the intake and make sure that the NG/LP pin is all the way to the NG side.
on Jul 22, 2014
I have a Generac 5000 Watt Power Plus Mod-00413-0
Does this have an oil filter and if so wich one do i need ?!?
Regarding the advice about "Flashing" a generator.
Do you people even know what that means?
What you are doing is messing with the capacitor that is part of the voltage conversion. Likely you are burning any shorts out of the capacitor. Has noting to do with the fields or coils or rectifier.
So if you are having issues then test the capacitor and replace it.
Try your flashing and see if you don't fry the rectifier.
It amazes me that people will blindly follow something they don't understand "hoping" that something good will happen.
But if a new generator is what you want then give your old one away instead of trashing it.
on May 13, 2020
Generac 11kw overspeed changed ignition coil still going into overspeed code
During engine cranking and operation the controller receives AC
voltage and frequency signals from the ignition magneto via Wire
18. Should the speed exceed approximately 72 Hz (4320 RPM),
the controller's logic will de-energize the "run relay" (internal to
the controller). The relay contacts will open terminating engine
ignition and closing the fuel shutoff solenoid; the engine will
then shut down. This feature protects the engine and alternator
against damaging over speeds. During cranking the RPM signal
generated by the magnetos is used to terminate engine cranking.
on May 09, 2020
Error code 1518 on a generac generator
If you have a Generac Generator which fails to start during a power outage and gives an Error Code 1518 - RPM Sense Loss you can try and manually get the generator restarted very simply. ... The generator should wait 5 seconds and then try and auto-start up to 3 times.
on Mar 25, 2020
Not finding what you are looking for?