Question about Mitsubishi Heating & Cooling
...discharge air temperature of a heat pump as compared to a fossil fueled heating supply, it is sometimes difficult to decide what mode they are in by feeling the air temperature. Fossil fueled heat ...
...rise of standard compressor discharge temperature. If over 105°C check refrigerant charge. If over charged release some gas./ Condenser block clean it./ Less rpm f.motor-replace
Error code ck 33 Excessive rise of standard compressor discharge temperature. If over 105°C check refrigerant charge
...-Excessive rise of standard compressor discharge temperature. If over 105°C check refrigerant charge. Over charged, release little gas still to normal PSI. If condenser full of debris, clean
...discharge temperature too high. If over 105°C, check refrigerant charge. Check and rectify the followings: If over charged-release some gas./If less rpm of fan motor-replace capacitor./Condenser ...
...? 6) unit is stoped P8 eroor code ? P8 error is abnormal pipe temperature indoor. If you are running it on heating P8 error will appear because the disc pressure is too high. It could be
...temperature of return air at inlet filters and measure temp. of discharge air at grilles. This temp diff. should be 14 to 18 C. with fan on hi speed. If temp diff. is less than this, suspect lack of ...
...Discharge pipe temperature error. Is there an easy fix?Thanks!! Please count timer flashing still pause.Basing on number of flashing will exactly mean the problem and can be solved. Awaiting for your ...
Question about Fujitsu Heating & Cooling
...discharge temperature, which translates to overheating outdoor unit. If this error code remains after a hard power reset, it's time to pick up the phone. Either you have a refrigerant leak which has ...
342 questions posted
Usually answered in minutes!