Cozy wall heater does not turn on
Hi, I will walk you through to check the stat. Pull off the cover 1st. You will need a screwdriver, a small one. Could be slotted or phillips. Loosen all of the screws you can see until the t-stat comes off. You have 3 sections counting cover. You will now see the sub-base and wires. You should have only 2 wires to the stat. You will need a piece of scrap insulated wire, even a piece of old speaker wire twisted togeter at each end will work. No worry of shock. Just jump or touch across the 2 terminals and hold them on and if it fires up and comes on, the thermostat is the fault. More then likely that will be the problem. Any hardware store will have one. Get a heat milivolt only, even if the salesman trys to sale you a heat/cool 24 volt stat which will work, but will cause problems in the future. I am sure it is stat. If not, contact me and I will walk you through what else would cause this. If the pilot is on, there is no ignitor on this furnace, either a thermopile generator or a thermocouple, a high limit switch and the main gas valve. Keep me posted, it will only take you a few minutes to test the t-stat. Let me know.
on Dec 11, 2018