Question about Energizer Rechargable Battery with Charger
Dont know how the wires go back. have red, black and ground from motor. have red, black, white and ground coming from house. need to go into cfci duplex receptacle and on/ off flip switch.
First and foremost, you need to check the Motor's voltage requirements, and match it to the voltage of the GFI you have connected to the House current.
The best way to do this is to use a volt meter at the GFI receptacle. Although it's likely the voltage at your GFI receptacle is 120Volts AC, you shouldn't guess on this. If you know what circuit breaker this GFI is using to get power.... you may be able to determine the GFI's voltage if you know how to distinquish between a single pole breaker and a two pole breaker (120Volts is derived from a sigle pole breaker, 240volts from a two pole breaker-which is twice the size of a single pole breaker).
Now the Motor: Most common Pool Motors are dual winding motors, on which, the voltage requirement could be changed to match the voltage supplied. On such a motor, there's a compartment where the cord is attached. Within this compartment, there's a configuration of screws or terminal points, and a related schematic which depicts the proper connections for each of the voltage options. By following these schematics, you will know how to connect the motor based on the available voltage supplied by your GFI protected receptacle.
Posted on Mar 23, 2009
I assume you mean a gfci recepticle? If this is the case you need to take the black wire from the house and pigtail it to go to both the recepticle (Black / Line) and one line side screw of the switch. The white wire from the house goes directly to the line/white side of the recepticle. Also pigtail the ground to go to the green screw on the recepticle, the green screw on the switch, the green wire from the motor, and the ground screw on whatever box you're using. When you purchase the switch make sure you get a two pole switch rated for at least the amperage of the motor. The red wire from the house and the black wire from the pigtailed black will go to the two line side screws of that switch. The red and black from the motor will go to the two screws on the load side of that switch. Make sure to ground everything properly being so close to water. The cover needs to be sealed securely and I recommend the cover that has the lever to activate the switch as opposed to the little door over the switch handle. Also make sure the two breakers supplying those two circuits have a handle that turns them both off at the same time.
Posted on Nov 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 07, 2014 | AO Smith A O Smith Motors A O Smith 2hp...
Sep 03, 2014 | Pool & Spa
Jun 21, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
May 05, 2010 | Smith AO Pool Pump Motor
Aug 04, 2009 | Kitchen Ranges
Jul 31, 2009 | Pool & Spa
Jul 23, 2009 | Pool & Spa
Jul 03, 2009 | AO Smith 1 1/2 HP 115/230V 56C Replacement...
Jun 02, 2014 | Energizer Rechargable Battery with Charger
161 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: