I am rehanging the ceiling fan in my daughters room and do not have the original instructions for connecting the wires and the wires are not labeled.
From the ceiling i have green, yellow, and a bare copper wire. I have a ground attached to the ceiling fan bracker.
Black from the ceiling goes to black from the fan White from the ceiling goes to white from the fan Red from the ceiling goes to blue on the fan...if you don’t have a red, connect the blue wire to the black from the ceiling. The blue is power to the light kit, and sometimes has a separate wall switch, hence the different color. If not, you control the complete power to the fan with the single wall switch (black and white wires) and then control the fan/light with the pull chains
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
BEFORE YOU PERFORM ANY CONNECTIONS BE SURE THAT THE CORRECT CIRCUIT BREAKER FOR THE BOX HAS BEEN TURNED OFF! You must check for voltage between the white and black wires at the ceiling box with each of your two wall switches toggled up or down ONE AT A TIME! The green wire in the ceiling box (or bare copper wire) is your ground wire and should be connected to the green wire of the fan, and also should be mechanically connected to the electrical box by a screw or clip. If your system was wired correctly you should find that it already is connected to the box. The white wire in the ceiling box is your neutral wire, so any and all white wires from the fan should be connected to it. You may have one for the fan motor and one for the light kit if there are two separate whites from the fan. Again, they may already be connected together in the fan/light assembly. The black wire in the ceiling box is switched on and off from either of the two switches in the room, which I assume are located near two different doors to the room. These are called "three-way switches". They are not marked "on" and "off" on the toggle like any single-light switches in your home. That is why you must check for power at the ceiling box with the switches in each position one at a time to make sure that the circuit is de-energized. Now for the connections: You will need to connect both the red and black wires from the fan to the black wire from the electrical box. The black wire in your ceiling box is your "hot" wire and will provide power to both the fan motor (black wire) and to the light through the red wire--(sometimes this wire is blue, for others who are following this post). With this arrangement, your fan and light will only operate with one or the other of your three-way switches completing the circuit from your breaker box. You will have to use the pull chains on the fan to control the fan and lights. So you will probably want to leave the light "pulled on" so that you can control the room lighting from either of your three-way switches, and operate your fan speeds from the pull chain. However, if you want your fan only on at night you will have to "pull off" the fan's light switch. You may find all this switch flipping and chain pulling an inconvenience. If so, hire an electrician to install wiring so that the ceiling box will be "hot" all the time to the fan's black wire and the fan will therefore be operated by the pull chain only, and the light kit will be controlled by either of the three way switches, via the fan's red (or blue) wire. One other caveat before you begin: you must make sure that the ceiling box is rated for and mounted sturdily so that it will support the weight of the fan and light kit. Many ceiling boxes are designed and mounted to support only a light-weight fixture. You don't want your fan to come crashing down from the ceiling!
Black is for the fan motor which you connect to black(hot), black/white is for the light which you connect to the switched lead in the ceiling, the white lead from the fan goes to the neutral lead in ceiling, and tjhe green wire is earth ground and goes to the box screw in the ceiling
Make sure to click breaker completely over to one side and then click all the way back to reset.
Yes, breakers go bad.
You can check your breaker in a simple way.
Turn main breaker OFF. Mark daughter's breaker. Take cover off breaker box. The main breaker will still have power on the lugs where big wires connect. Rest of box will have no power. Notice that each 120 volt breaker has a wire connected to end of breaker. Use screwdriver and tighten this wire. If screw is already tight, then loosen screw and pull wire out, and move wire to another breaker marked with same amperage. For example if daughter's breaker is 20, then move wire to another 20. Now there will be two wires connected to that breaker. Turn power ON and see if daughter's room is restored. This set up will work fine until you have time to replace breaker with same brand as marked on breaker box, usually available at home center (if available).
If power is not restored by moving wire, then there is a loose wire inside a junction box located in daughter's room. Test each receptacle in room to confirm that nothing on that circuit has power. If some receptacles have power, start opening other receptacle boxes looking for loose wire, especially at the quick-connects where wires stab into back of receptacle device. If whole circuit is off, then to isolate location of loose wire, start at the ceiling box, and see if there is a loose black or white wire. Most electricians run wire from breaker to the ceiling box, and then other wires spread out from there and go box to box until each box has a black and white wire that connects back to original breaker.
OK, the wires coming from the top of the fan are going to go into the junction box in your ceiling. Out of the ceiling, you should have a white wire, a black wire, and a green or bare copper ground wire. Make sure your power is off at the fan. Your wires coming out of the fan should be white, black, blue, and a green ground wire. Pull the wires through the top of your fan, and connect the white to the white in the ceiling, the black and blue wires from the fan to the black wire in the ceiling, and then connect your ground wires together. Make sure you use wire nuts and twist them firmly onto the ends of the wires. If you happen to have a red wire coming out of the ceiling as well, just put a wire nut on it and stuff it back into the ceiling box. The blue wire is what works your light kit, and the black is for the fan. Hope this helps you!
Green and copper are the ground wires and I believe you can connect both these to the green wire from the fan (I only have the copper wire in the actual ceiling box). Black and Red can be treated as both black and both can be connected to the black wire from the fan (this is what I did in all my fans and it worked). White is the neutral wire and can be connected to the white wire from the fan (this is what I did in all my fans and it worked).
My ceiling box has the copper, red, black, and white wires. The ceiling plate for the fan I bought had a green wire. I connected the green wire from the ceiling plate and the copper wire from the ceiling box to the green wire from the fan.