Question about Compaq UPS T1000h (242688-002) UPS System
When we have failure on electric system, our UPS T1000h take over the load of our main computer. But after 15 sek. starts our electric generator to take over the mains and then become the problem. The main fuse (10Amp.) on our UPS break down. This happens every time, when el.generator starts. Without el.generator, UPS works well.
In our organisation we have other UPS systems and all doing fine.
I had a problem like this one, check the voltage from the generator , if the output from the generator is to high (over 240 Volts european standard voltage), the voltage protection (VDR resistors ) will brake the fuse to protect your UPS.
and also check the frequency of the generator, it has to be very stabile around 50HZ (european standard frequency)
Posted on Sep 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 22, 2013 | MGE Computers & Internet
Mar 19, 2011 | APC APS BackUPS CS 650VA 400W 230V DB9...
Jan 04, 2011 | Compaq UPS T1000h (242688-002) UPS System
Dec 16, 2010 | Emerson PowerSure Personal 500VA...
Jul 08, 2010 | Compaq UPS T1500 UPS System
Sep 25, 2009 | Compaq 204015-001 - UPS T700 - UPS - 700...
Jul 24, 2009 | APC Smart-UPS 1000VA UPS System
Dec 04, 2008 | APC (BH500NET) UPS System
Jul 26, 2007 | Compaq UPS R3000 (242705-001) UPS System
Apr 25, 2017 | Avira Computers & Internet
336 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: