Question about Bryant Heating & Cooling
Ifs its a small humming sound,then its the contactor pulling in. But if it a loud humming sound then its the compressor kicking in. and the fans not, try to take something long and turn the blades on the fan, if it takes off and run then your capacitor is shot or swollen at the top,which was cause by power surge. Take-off and replace with the same mfd. writings ,on the outside of can. Also check for blown fuses or tripped breaker . the fuses should be in the disconnect box on the wall, or the breaker in the breaker box.. Older house has fuses instead of a breaker box!
Posted on Sep 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Aug 13, 2011 | Heating & Cooling
May 31, 2011 | Heating & Cooling
Sep 17, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 26, 2010 | Carrier 36KCARMS Air Conditioner
May 30, 2010 | Carrier 38CKC042 Air Conditioner
Jan 19, 2010 | Samsung AW0603B Air Conditioner
Jun 17, 2008 | Goodman Heating & Cooling
May 06, 2008 | Weather King 10AJA2501AH Air Conditioner
324 people viewed this question
Usually answered in minutes!