Question about Air Conditioners
Ceck if there is spark.
If there is no spark, then the igniter may need replacement. Testing is done reading volts.
If there is spark, then either valve coils or flame sensor may be causing the problem.
Valve coil can be tested reading Ohms at coil contacts (power off first). If the coil reads infinite Ohms, then it must be replaced.
If coils are good, then the flame sensor must often be replaced. This is more difficult to test.
In some case the valve may be mechanically faulty (stuck), or wiring and control board may be responsible of the problem.
Posted on Aug 16, 2010
Tips for a great answer:
Aug 21, 2014 | Air Conditioners
Jul 30, 2013 | Air Conditioners
Jul 18, 2011 | Air Conditioners
Nov 01, 2010 | Air Conditioners
Sep 05, 2010 | Air Conditioners
Jun 29, 2010 | Air Conditioners
Jan 30, 2009 | Maytag M6Y18F7A Air Conditioner
Oct 06, 2008 | Air Conditioners
Jun 10, 2008 | Air Conditioners
Dec 05, 2016 | Air Conditioners
260 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: