Question about Heating & Cooling
F20 is a flow sensor error. Can be due to a defective sensor/ not correctly fitted, or you may have poor circulation, a big difference in flow and return temperatures, can sometimes make the boiler think it has a defective sensor, check good circulation through system, or if you have thermostatic radaiators valves on every single radiator, take 1 head off, as if you dont have a bypass fitted, it needs a radiator as a bypass circuit
Posted on Mar 03, 2009
Checkout the co. website.!
Posted on Aug 30, 2008
Check the internal rubber connection hoses on the flow and return, if they feel crunchy, that's probably your problem.
Posted on Sep 22, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 03, 2013 | Heating & Cooling
Nov 11, 2012 | Computers & Internet
Mar 02, 2012 | Heating & Cooling
Sep 29, 2010 | Heating & Cooling
Jul 16, 2009 | Water Heaters
Mar 25, 2009 | Water Heaters
Dec 31, 2008 | Heating & Cooling
4,305 people viewed this question
Usually answered in minutes!