Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
I am in Florida, and here lately when it gets real hot in the afternoon, my compressor shuts down. Outside unit fan is running, fan inside is running, but compressor wont pump. Carrier system installed in 93. Installed a focuspro 5000 thermostat and had the unit charged and then this started. I just had to install a new contactor switch this week also. Any idea what is going on?
This could be low freon which would cause a low pressure swirch to turn off the compressor. Other causes could be dirty coils (inside and out) which would reduce airflow causing high pressure which would cause the high pressure switch to turn off the compressor.
If the coils are clean, take a thermometer and measure the difference between the outside ambient tempature and the temerature of the hot air coming out of the compressor unit. There should be at least 20 degrees difference, if not it probably is low freon.
Posted on Oct 17, 2008
Make sure you provide shade for your unit. It may help keeping it cool.
Posted on Sep 17, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 19, 2015 | Heating & Cooling
Jul 28, 2012 | Dometic Rooftop RV Air Conditioner
May 25, 2012 | 2000 Dodge Grand Caravan
Jul 25, 2011 | Goodman Heating & Cooling
Aug 14, 2009 | Heating & Cooling
Jun 11, 2009 | Goodman CKL60AR60 Air Conditioner
May 19, 2009 | LG Heating & Cooling
Jul 19, 2008 | Goodman CLQ36AR49 Air Conditioner
148 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: