Question about Lutron CA-1PSH-LA Almond Claro Switch
Hi .. If you have only one wire on the switch, then there is another wire that has broken away from the connection. or a wire has become disconnected. There needs to be two wires for the switch to function. Look inside the wall box and see if you can locate the other wire. Then use the two wires to connect to your new switch.
Posted on May 03, 2010
First check and see where the white wires to the switch originate from in the lighting circuit. If it is from the black or (HOT) wire of the lighting circuit. It is connected correctly. Put black electrical tape on the wires near the switch. If the white wires going to the switch originate from or are connected to the white wire ( Circuit Neutral ) in the lighting circuit. This is wrong never put a switch in the neutral side of any circuit. Connect one white wire that is going to the switch to the black (Hot ) wire in the lighting circuit. Then connect the other white wire coming from the switch to the light or object to be operated. Tape this with black tape near the switch and near the object to be operated,for identification later on. BUT ABOVE ALL. BE SURE TO TURN OFF THE POWER BEFORE WORKING ON ELECTRICAL CIRCUITS.
Posted on Aug 29, 2008
Switches always connect to hot (black) wires. In some cases you may find a white wire with the end taped black denoting it is serving as a hot (black) wire. Or you may find a white wire connected to the switch. If that's the case, the prior electrician did not properly mark the wire and it should be marked as a black wire. Wrap the end with black electrical tape after disconnecting.
Posted on Aug 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 05, 2012 | Home
Jan 14, 2011 | Cooper Lighting Lighted Switch
Nov 17, 2010 | Leviton COMBINATION SINGLE POLE TOGGLE...
Nov 13, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Sep 14, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Apr 08, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Mar 02, 2010 | Electrical Supplies
Apr 12, 2009 | Leviton 8299 Combination Switch / Smart...
Mar 23, 2009 | Electrical Supplies
Jan 25, 2009 | Hunter 28096 Westminster 52" Ceiling Fan...
224 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: