Question about Heating & Cooling
Check the hot water temperature setting, maybe its too high! or raise the psi relief valve by buying a higher setting! Thank-you-very- much!
Posted on Aug 27, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 11, 2015 | Water Heaters
Hot water pressure relief valves serve two functions. The first is to remove high-pressure water from the hot water tank. The second function is to act as a high temperature valve to remove water that exceeds a predetermined point for the valve. Both of these relief settings are preset at the valve factory. Many pressure relief valves will come with a metal tag that identifies these release points. If you're attempting to remove the hot water heater pressure relief valve, pay careful attention to ensure that you replace with the correct valve.
Your hot water heater has a pressure relief valve safety mechanism. When pressure inside the water tank exceeds certain limitations, the valve opens up to allow the pressure to be released. A faulty pressure relief valve will not release excess pressure, which could cause extensive damage to your home. You should test the hot water heater pressure relief valve once every six months to ensure proper operation. If the pressure relief valve fails the test, replace the valve with a new one immediately
Locate the pressure relief valve on your hot water heater. The pressure relief valve has a lever handle on top with a drain pipe attached to it. The pressure relief valve is most often on the side of the water tank toward the top. Newer models of hot water heaters have the pressure relief valve on top of the water tank.
Inspect the area around the pressure relief valve for signs of leaking water. If there is leaking water near the relief valve connection, replace the relief valve. If no leaking is evident, proceed with testing the pressure valve.
Examine the area below the pressure relief valve drain pipe. Most water heater closets either have a drain in the floor below the pipe or the pipe is inserted into another pipe to direct the water out of the home. If the end of your drain pipe is not in another pipe or there is no drain in the floor, place a bucket under the drain pipe to catch water when you test the pressure relief valve.
Pull the lever handle on the top of the pressure relief valve up with your fingers. A working lever will lift up without difficulty.You should begin to hear water going through the drain pipe. Slowly release the lever to shut off the pressure relief valve. The pressure relief valve is good. If you did not hear water running through the drain pipe, lower the lever on the pressure relief valve and replace the valve. If the lever is difficult to raise, do not force the lever. Replace the pressure relief valve.
Feb 04, 2011 | Whirlpool Water Heaters
Nov 17, 2010 | RTO Atwood Water Heater - 6 Gal LP
Jan 13, 2018 | Heating & Cooling
Nov 11, 2007 | Heating & Cooling
Apr 21, 2018 | LG Heating & Cooling
42 people viewed this question
Usually answered in minutes!