Question about Air Conditioners
You probably have a bad thermocouple/pilot generator. This is a tube that is in the pilot flame when the pilot is lit. If the gas valve doesn't get a good reading from it, the gas valve won't allow ant flow. They are easy to replace, a thermocouple has a copper tube that inserts into the body of the gas valve, a pilot generator has two wire leads. The gas MUST be turned off while you change it out. If it's a tube type (thermocouple), be careful not to kink the copper tube during installation.
Posted on Aug 26, 2008
Tips for a great answer:
Sep 10, 2011 | Air Conditioners
Jun 22, 2011 | Air Conditioners
Mar 21, 2011 | Air Conditioners
Feb 20, 2011 | Air Conditioners
Jan 20, 2011 | Air Conditioners
Dec 23, 2010 | Air Conditioners
Nov 06, 2010 | Ruud UAPA024 Air Conditioner
Apr 05, 2009 | Air Conditioners
Jan 11, 2009 | Air Conditioners
67 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: