Question about Heating & Cooling
You probably have a bad thermocouple/pilot generator. This is a tube that is in the pilot flame when the pilot is lit. If the gas valve doesn't get a good reading from it, the gas valve won't allow ant flow. They are easy to replace, a thermocouple has a copper tube that inserts into the body of the gas valve, a pilot generator has two wire leads. The gas MUST be turned off while you change it out. If it's a tube type (thermocouple), be careful not to kink the copper tube during installation.
Posted on Aug 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2015 | Heating & Cooling
on Mar 14, 2011 | Heating & Cooling
Dec 03, 2012 | RTO Suburban Rv Water Heater Dsi Gas Valve...
Nov 08, 2012 | Heating & Cooling
Aug 26, 2012 | Water Heaters
Jan 29, 2011 | Heating & Cooling
Dec 19, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Nov 06, 2010 | Ruud UAPA024 Air Conditioner
Feb 06, 2010 | Vulcan GR45 Deep Fryer
Jul 09, 2009 | Northern Tool Water Heaters
67 people viewed this question
Usually answered in minutes!