Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
I had a brown out so I turned off the air. The power came back on and I came home and turned on the air conditioning and the outside unit is working but the furnace doesn't blow the cold air into the house.. I have checked for frozen lines and there are none. I turn the air off and the fan to on and there is air coming out of the vents inside the house so I turned the air on and then the air quits coming out of the vents. Please help:)
This only could 1--2 things, a bad circuit board fan relay or bad thermostat. To check for bad thermostat, take off the front cover to reveal the 4-wire terminial and jump the red-wire (power)-cool,(yellow -y or blue)--- green--fan white-(heat)..........red to yellow-or y=cool. Thank-you-very-much!
Posted on Aug 25, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 15, 2014 | Goodman Heating & Cooling
Jan 04, 2014 | Covercraft 2001 Dodge Grand Caravan -...
Sep 01, 2009 | Heating & Cooling
Jun 22, 2009 | Coleman Heating & Cooling
Jun 03, 2009 | Goodman CLJ30AR32 Air Conditioner
May 28, 2009 | Heating & Cooling
Jun 24, 2008 | Ruud UAKA030 Air Conditioner
May 22, 2008 | Heating & Cooling
May 03, 2008 | Ruud Handler Air Conditioner
282 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: