Question about Ruud UBHC Air Conditioner
There is ice all over the coils of the handler in the garage. we have checked the blower and start relay
1. Check the entrance filters to unit.
2. Check the fan to make sure it is moving air.
3. Make sure floor vents not closed off.
If these dont correct the problem you may a leak, which has caused a low charge. When this happens the refrigirant level drops creating a freezing condition in the evaperator coil. Hence it freezes up.
Hope this helps you
Posted on Aug 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 17, 2013 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Sep 13, 2011 | Heating & Cooling
Jun 29, 2011 | Carrier 38CKC060 Air Conditioner
May 25, 2011 | Amana Heating & Cooling
Jan 18, 2011 | Weather King 10PJA2501AH Air Conditioner
Jun 14, 2010 | Carrier 38CKC036 Air Conditioner
Jan 12, 2010 | Heating & Cooling
Oct 27, 2009 | Heating & Cooling
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: