Question about Goodman Heating & Cooling
Posted on Aug 28, 2008
With the jumper inplace does the compressor start? What about without? Unless you have more than one transformer you should leavethe jumper.
Posted on Dec 06, 2008
Most of the cases when tou heard a click on and off is aproblem with the compresor that goes off on overload, when the compresor try to start and is stuck , burned or the starting coil inside it is open it's overheat and goes off by the thermo bimetal switch.Also could be the capacitor, to check it you need a capacitor tester,but if you don't have it you can try to put anew one (no more than 10 $) and see what happend if still the compresor is getting hot and won't turn on it's burned, jamed or open , and you have to replce it ,if it's less than a year old it should be under warranty but if not is an expensive job and you better get a new unit.
Posted on Apr 15, 2009
Sounds like a bad capacitor. They can be bad and the fan will still run. Turn off power and check for burnt wires on the top of the contactor going to the capacitor or on the top of the capacitor.. Check terminals on the compressor also. When capacitors go bad they are slightly swollen. They can also look good and be bad . Could be compressor but start with capacitir and wires. IWork on a lot goodman units. Most of the time it is the cap.
Posted on Jun 03, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
Tips for a great answer:
Oct 28, 2011 | Goodman GMS90703BXA Heater
Aug 24, 2011 | Heating & Cooling
Jun 23, 2011 | Heating & Cooling
Jun 20, 2011 | Goodman Heating & Cooling
May 26, 2010 | Goodman CLQ36AR49 Air Conditioner
Feb 07, 2010 | Goodman GMS90703BXA Heater
Oct 07, 2009 | Goodman Heating & Cooling
May 01, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 06, 2009 | Heating & Cooling
158 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: