Question about Ruud UBHC Air Conditioner
We are buying a house with a ruud upka-030jas ac unit. we have tried to turn it on. it blows the fan on in the inside of the house but the outside unit does not come on. there is no manual that we have found. is there a special trick or may something be wrong?
serial# 4919 m2293 073
Access the compressor common, start, run terminals. Disconnect the wires from them and test them with an ohm meter. You should have a measurable resistance between each terminal and infinite from any of the terminals to the compressor case. If that is good you want to check if you have a starting relay if the relay is bad the compressor will have very high amps and then go off on either the thermal overload of circuit breaker.
Posted on Dec 17, 2012
Bad capacitor or low pressure switch or maybe safety switch on condesate pump or ptrap
Posted on Jun 04, 2012
Check if you are getting 24 volts to you contactor coil on your condensing unit. If you are that means your problem is in your condensing unit check voltage going to your condensing unit it will be usually 208 to 230 v.
Posted on Aug 25, 2008
No special tricks alyson.....prolly just a breaker or fuse.check the main panel for a turned off breaker and at the unit there's a disconnect box that may have a bad fuse.
Posted on Aug 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 20, 2014 | Ruud Heating & Cooling
Sep 03, 2011 | Ruud Heating & Cooling
Feb 23, 2010 | Ruud Matching Split Air Conditioner
Jul 18, 2009 | Ruud Central System Air Conditioner
Jul 10, 2009 | Heating & Cooling
Jun 29, 2009 | Heating & Cooling
Jun 07, 2009 | Ruud UBHC Air Conditioner
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
May 25, 2009 | Ruud Central System Air Conditioner
Sep 01, 2008 | Ruud Heating & Cooling
221 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: