Question about Heating & Cooling
visit this web site..this should be very similar to your remote.. http://www.abergas.co.nz/anytime/pdf_files/anytime48b23cc130447p314.pdf
Posted on May 28, 2009
If there is no air coming through all of ducts, there are several things to consider. If you turn your thermostat to fan on, does air come out? If so you may have a switching|thermostat problem. May need to change out, not really hard you just have to turn off electric mark wires as you remove and turn back on. If nothing changed, make sure the circuit breaker has tripped, sometimes its hard to tell so flip it all the way off then back on. Now try to turn on again. If it comes on you need to find out why it's tripping the breaker, merely resetting it can pose a danger for the future. Professionally servicing the unit is important to the longevity of the unit. Now if you find out that unit is coming on but no air is coming out, it could well be that a duct has blown free and is spilling into attic or crawl space. Sometimes the unit forms an ice block in the evaporative area of the unit. In this case it would need quite some time off to thaw. Also the fan motor may be burned out. In that case you would hear part of the unit working with no output. These are a few of the most common problems with this condition.Most of which needs to be addressed by a Tech
Posted on Jul 15, 2009
SOURCE: got a pyrox comfort control
on the reset switch there should be a temp. cut out take a temp. reading and see if it is realy getting as hot as the switch is rated for maybe the switch is bad
Posted on Aug 11, 2010
SOURCE: I have a new LG
Reverse or open phase. Check all 3 phases are present and correct. If correct voltage appears at all three phases, swap any two to cure the fault. Thanks. Helpful?
Posted on Feb 12, 2011
Tips for a great answer:
May 26, 2015 | Heating & Cooling
Apr 25, 2015 | Heating & Cooling
Aug 21, 2011 | Heating & Cooling
EACH OF THE FOLLOWING STATUS CODES IS A TWO DIGIT NUMBER WITH THE FIRST
DIGIT DETERMINED BY THE NUMBER OF SHORT FLASHES AND THE SECOND DIGIT BY
THE NUMBER OF LONG FLASHES.
11 NO PREVIOUS CODE - Stored status code is erased automatically after 72
hours. On RED LED boards stored status codes can also be erased when power
(115 VAC or 24 VAC) to control is interrupted.
12 BLOWER ON AFTER POWER UP (115 VAC or 24 VAC) -Blower runs for 90
seconds, if unit is powered up during a call for heat (R-W closed) or R-W opens
during blower on-delay.
13 LIMIT CIRCUIT LOCKOUT - Lockout occurs if the limit or flame rollout switch is
open longer than 3 minutes.
- Control will auto reset after three hours. - Refer to #33.
14 IGNITION LOCKOUT - Control will auto-reset after three hours. Refer to #34.
21 GAS HEATING LOCKOUT - Control will NOT auto reset.
Check for: - Mis-wired gas valve -Defective control (valve relay)
22 ABNORMAL FLAME-PROVING SIGNAL - Flame is proved while gas valve is
de-energized. Inducer will run until fault is cleared. Check for:
- Leaky gas valve - Stuck-open gas valve
23 PRESSURE SWITCH DID NOT OPEN Check for:
- Obstructed pressure tubing. - Pressure switch stuck closed.
24 SECONDARY VOLTAGE FUSE IS OPEN Check for:
- Short circuit in secondary voltage (24VAC) wiring.
31 PRESSURE SWITCH DID NOT CLOSE OR REOPENED - If open longer than
five minutes, inducer shuts off for 15 minutes before retry. Check for:
- Excessive wind - Proper vent sizing - Defective inducer motor
- Low inducer voltage (115VAC) - Defective pressure switch
- Inadequate combustion air supply - Restricted vent
- Disconnected or obstructed pressure tubing
- Low inlet gas pressure (if LGPS used)
If it opens during blower on-delay period, blower will come on for the selected
33 LIMIT CIRCUIT FAULT - Indicates a limit, or flame rollout is open. Blower will
run for 4 minutes or until open switch remakes whichever is longer. If open
longer than 3 minutes, code changes to lockout #13. If open less than 3 minutes
status code #33 continues to flash until blower shuts off. Flame rollout switch
requires manual reset. Check for: - Restricted vent
- Proper vent sizing - Loose blower wheel - Excessive wind
- Dirty filter or restricted duct system.
- Defective blower motor or capacitor. - Defective switch or connections.
- Inadequate combustion air supply (Flame Roll-out Switch open).
34 IGNITION PROVING FAILURE - Control will try three more times before lockout
#14 occurs. If flame signal lost during blower on-delay period, blower will come
on for the selected blower off-delay. Check for: - Control ground continuity
- Flame sensor must not be grounded
- Oxide buildup on flame sensor (clean with fine steel wool).
- Proper flame sense microamps (.5 microamps D.C. min., 4.0 - 6.0 nominal).
- Gas valve defective or gas valve turned off - Manual valve shut-off
- Defective Hot Surface Ignitor
- Low inlet gas pressure
- Inadequate flame carryover or rough ignition
- Green/Yellow wire MUST be connected to furnace sheet metal
45 CONTROL CIRCUITRY LOCKOUT Auto-reset after one hour lockout due to;
- Gas valve relay stuck open - Flame sense circuit failure
- Software check error
Reset power to clear lockout. Replace control if status code repeats.
If status code recall is needed, briefly remove then reconnect one main limit wire to display
stored status code. On RED LED boards do not remove power or blower door before initiating
status code recall. After one status code recall is completed component test will occur.
Thanks for Choosing FixYa.
Oct 05, 2010 | Heating & Cooling
Aug 11, 2010 | Heating & Cooling
Feb 18, 2010 | Heating & Cooling
Dec 04, 2009 | Goodman Heating & Cooling
Jul 08, 2008 | Heating & Cooling
Jul 06, 2008 | Heating & Cooling
51 people viewed this question
Usually answered in minutes!