Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
visit this web site..this should be very similar to your remote.. http://www.abergas.co.nz/anytime/pdf_files/anytime48b23cc130447p314.pdf
Posted on May 28, 2009
If there is no air coming through all of ducts, there are several things to consider. If you turn your thermostat to fan on, does air come out? If so you may have a switching|thermostat problem. May need to change out, not really hard you just have to turn off electric mark wires as you remove and turn back on. If nothing changed, make sure the circuit breaker has tripped, sometimes its hard to tell so flip it all the way off then back on. Now try to turn on again. If it comes on you need to find out why it's tripping the breaker, merely resetting it can pose a danger for the future. Professionally servicing the unit is important to the longevity of the unit. Now if you find out that unit is coming on but no air is coming out, it could well be that a duct has blown free and is spilling into attic or crawl space. Sometimes the unit forms an ice block in the evaporative area of the unit. In this case it would need quite some time off to thaw. Also the fan motor may be burned out. In that case you would hear part of the unit working with no output. These are a few of the most common problems with this condition.Most of which needs to be addressed by a Tech
Posted on Jul 15, 2009
SOURCE: got a pyrox comfort control
on the reset switch there should be a temp. cut out take a temp. reading and see if it is realy getting as hot as the switch is rated for maybe the switch is bad
Posted on Aug 11, 2010
SOURCE: I have a new LG
Reverse or open phase. Check all 3 phases are present and correct. If correct voltage appears at all three phases, swap any two to cure the fault. Thanks. Helpful?
Posted on Feb 12, 2011
Tips for a great answer:
May 26, 2015 | Heating & Cooling
Apr 25, 2015 | Heating & Cooling
Mar 02, 2015 | Heating & Cooling
Sep 22, 2011 | Maytag PYG4500A Gas Dryer
Aug 21, 2011 | Heating & Cooling
Jun 11, 2011 | Heating & Cooling
May 19, 2017 | Heating & Cooling
Aug 11, 2010 | Heating & Cooling
Apr 27, 2009 | Heating & Cooling
Jul 08, 2008 | Heating & Cooling
Jan 22, 2018 | Heating & Cooling
55 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: