Question about Goodman CKL30AR30 Air Conditioner
The fan system works but the unit outside does not. I can hear a slight electrical hom so it seams to be that power is getting to the unit outside but it is not running. I have reset the circut breakers. Is there another reset on the unit itself inside the actual box?
That is correct also. Down here in Tornado alley, we have lightning strikes all during the summer months, and from experience ,we mostly have tripped breakers and or exploded or swollen capicators or that little silver can. if it looks swollen at the top then it exploded and needs replacing.Also look in the outside disconnect box for blown fuses, oh yes ,the light humming noise comes from the contactor being pulled in by the inside 24volt system from the furnace. Thank-you very-much
Posted on Aug 25, 2008
Depending on where you live, there are electrical codes that require a 'disconnect' near the outside unit.. This is to be removed prior to servicing that unit and prevent the service person from getting injured if someone inadvertantly turned it on The humming sound you may be hearing may be the fan motor insise that unit, It is possible that the lightning strike generated a surge that damaged that fan motor winding.. With the protective screen removed and that unit disconnected from power.. try spinning the fan by hand to make sure it is free to turn, then reassemble everything and see if will start up. If it is a 220VAC system then you could also be missing one phase of power..You might want to contract an electrician for that aspect of troubleshooting. Be careful and goodluck..
Posted on Aug 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Jun 16, 2014 | GE Zoneline Deluxe Series Cooling &...
Aug 28, 2011 | Heating & Cooling
May 30, 2011 | Goodman Heating & Cooling
Mar 25, 2011 | Heating & Cooling
Jul 20, 2010 | Goodman CKL24AR24 Air Conditioner
Jul 09, 2010 | Carrier 38CKC048 Air Conditioner
May 27, 2010 | Dometic Rooftop RV Air Conditioner
Aug 09, 2009 | Heating & Cooling
it is high voltage section failure
better call skilled tech to fix it.
Oct 15, 2007 | RCA F32450 32" TV
Aug 06, 2011 | Goodman CKL30AR30 Air Conditioner
433 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: