Question about Randell Refrigeration 111'' Refrigerated 4 Door Pizza Prep. Table - Poly Cutting Board Top
Top of make table working but lower unit not.Blowing warm air
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a Randell 5ft
This unit uses Thermostat/Solenoid Valve Combination's to control the temperature
1. Rail 2. Bottom Storage
The way it works is the thermostat senses the need for cooling and energizes the solenoid valve. This allows refrigerant flow which cools the area it is controlling. Once the thermostat is satisfied the contacts open and the solenoid is de-energized closing the valve. If the solenoid is bad, the valve remains closed, no refrigerant flow, warm unit.
Test the solenoid coil (two wires) to see if voltage is present either with a volt meter, or remove the coil off the valve and place a screwdriver (insulated) through the coil hole and you should feel the pull like an electro-magnet (what a coil is).
Posted on Dec 05, 2010
Tips for a great answer:
Sep 23, 2011 | Heating & Cooling
Aug 10, 2011 | Dehumidifiers
Jul 31, 2011 | Whirlpool AD25BBK Dehumidifier
Jul 18, 2011 | Goldstar DH304 Dehumidifier
Jul 12, 2011 | Refrigerators
Apr 27, 2011 | True Refrigerated Sandwich Prep Table 72"...
Dec 05, 2010 | Randell Refrigeration 60'' Refrigerated 2...
Jun 22, 2010 | Randell Refrigeration 111'' Refrigerated 4...
Jan 13, 2009 | Heating & Cooling
235 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: