Question about Carrier Heating & Cooling
More than likely. Your fan motor is probably pulling to many amps. Observe your unit while it is not running. By way of turn the blades of the fan to feel if you experience any restriction. If so. Your fan motor is bad. There are other reason, like shortages, within the wiring, bad contactor, among others, however; check the fan motor first then conduct a thorough visual inspection.
Posted on Aug 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 10, 2012 | Goodman Heating & Cooling
Aug 21, 2011 | Heating & Cooling
Aug 03, 2011 | Goodman CKL49AR49 Air Conditioner
Jun 06, 2011 | Heating & Cooling
May 22, 2011 | Heating & Cooling
Sep 01, 2009 | Honeywell Heating & Cooling
Aug 17, 2009 | Heating & Cooling
Aug 17, 2009 | Dometic Rooftop RV Air Conditioner
Sep 08, 2007 | LG Art Cool LA121CNP wall/window Air...
30 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: