Question about Carrier Heating & Cooling
most time, you don't have to do anything because the default setting for wiring with fan speed already. if not, trace the motor wires from motor with red , white and black from motor fan to PL2 and PL1. the best is look at a diagram from your actual furnace.
Posted on Nov 09, 2008
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Nov 28, 2009
Tips for a great answer:
Nov 21, 2014 | GE Carrier Bryant Payne 1/3 Hp 115v Blower...
Nov 08, 2014 | Heating & Cooling
Sep 15, 2014 | GE Carrier Bryant Furnace 1/2 Hp Ecm...
Sep 07, 2014 | Heating & Cooling
Feb 03, 2013 | Intertherm E3EB-017H Furnace 17Kw 2
Nov 03, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 06, 2009 | Carrier Heating & Cooling
Nov 24, 2008 | Heating & Cooling
Sep 29, 2008 | Haier HWR06XC5 Wall/Window Air Conditioner
228 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: