Question about Rinnai RHFE-1004FA 38,400 BTU Energy Saver Ductless Heater - Natural Gas
Check for a blockage in the heat exchanger. Spiders love to make nests in these units. Remove the front cover and the two rectangular viewing ports on the front of the heat exchanger. Watch as the unit ignites. There are three burners you need to watch and the first one is in the center and hard to see. If there is flame but it goes out quickly, you have a blockage in the unit. Check the venting to make sure it is clear of debris.
Posted on Sep 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 15, 2011 | Rinnai RHFE-431FAIII 16,700 BTU Direct...
Jun 18, 2011 | Rinnai Heating & Cooling
Aug 18, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
May 05, 2010 | Rinnai EnergySaver 556 Air Conditioner
Jul 29, 2009 | Rinnai EnergySaver 556 Air Conditioner
Apr 27, 2009 | Heating & Cooling
257 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: